[Document(page_content='\n\n10\nEnergy\n3\n2018-01-01\n2018-01-01\nfalse\nUniform test method for the measurement of energy efficiency of commercial packaged boilers.\nÂ§ 431.86\nSection Â§ 431.86\n\nEnergy\nDEPARTMENT OF ENERGY\nENERGY CONSERVATION\nENERGY EFFICIENCY PROGRAM FOR CERTAIN COMMERCIAL AND INDUSTRIAL EQUIPMENT\nCommercial Packaged Boilers\nTest Procedures\n\n\n\n\n§\u2009431.86\nUniform test method for the measurement of energy efficiency of commercial packaged boilers.\n(a) Scope. This section provides test procedures, pursuant to the Energy Policy and Conservation Act (EPCA), as amended, which must be followed for measuring the combustion efficiency and/or thermal efficiency of a gas- or oil-fired commercial packaged boiler.\n(b) Testing and Calculations. Determine the thermal efficiency or combustion efficiency of commercial packaged boilers by conducting the appropriate test procedure(s) indicated in Table 1 of this section.\n\nTable 1—Test Requirements for Commercial Packaged Boiler Equipment Classes\n\nEquipment category\nSubcategory\nCertified rated inputBtu/h\n\nStandards efficiency metric(§\u2009431.87)\n\nTest procedure(corresponding to\nstandards efficiency\nmetric required\nby §\u2009431.87)\n\n\n\nHot Water\nGas-fired\n≥300,000 and ≤2,500,000\nThermal Efficiency\nAppendix A, Section 2.\n\n\nHot Water\nGas-fired\n>2,500,000\nCombustion Efficiency\nAppendix A, Section 3.\n\n\nHot Water\nOil-fired\n≥300,000 and ≤2,500,000\nThermal Efficiency\nAppendix A, Section 2.\n\n\nHot
rtdocs_stable/api.python.langchain.com/en/stable/modules/indexes/document_loaders/examples/web_base.html